Presented by Justin Biller, P.E., MCP, CFPS, CLSS-HC
Fire Protection and Life Safety Design
Applicable codes • International Fire Code • National Fire Protection Association (NFPA) codes • Georgia building codes • Local ordinances
Scope and purpose of codes and ordinances Special occupancies: health care facilities and others
General requirements and criteria • Change of use and /or change of occupancy • Hazard classifications
Life safety issues Design specifications and scenarios Evaluation and documentation
Means of Egress
Exit access, discharge and other components • Impediments to egress
Calculating and determining occupant loads • Gross vs. net
Arrangement of exits Equivalency discussion Case studies
Fire Protection Features and Equipment
Walls, signage Fire detection, alarm and communication systems Sprinkler systems
Continuing Education Credit Information
This seminar is open to the public and offers 6.5 PDHs to Georgia professional engineers and 6.5 Public Protection PDUs to Georgia architects. Educators and courses are not subject to preapproval in Georgia.
This seminar is approved by the American Institute of Architects Continuing Education System for 6.5 LU|HSW (Provider No. J885). Only full attendance can be reported to the AIA/ CES. Visit www.halfmoonseminars.org for complete AIA/CES information under this course listing.
Architects and engineers seeking continuing education credit in other states will be able to apply the hours earned at this seminar, in many cases. Refer to specific state continuing education rules to determine eligibility.
The International Code Council has approved this event for .65 CEUs in the specialty area of Fire.
This course offers a non-credit continuing education opportunity to construction contractors. It has not been approved by any state contractor licensing entity.
Attendance will be monitored, and attendance certificates will be available after the seminar for most individuals who complete the entire event. Attendance certificates not available at the seminar will be mailed to participants within fifteen business days.
Embassy Suites – Galleria
2815 Akers Mill Road SE Atlanta, GA 30339 (770) 984-9300
Tuition $289 for individual registration $269 for three or more registrations. Included with your registration: Complimentary continental breakfast and printed seminar manual.
Receive a reduced tuition rate of $101 by registering to be our on-site coordinator for the day. For availability and job description, please visit www.halfmoonseminars.org.
How to Register
• Visit us online at www.halfmoonseminars.org • Mail-in or fax the attached form to 715-835-6066 • Call customer service at 715-835-5900
Cancellations: Cancel at least 48 hours before the start of the seminar, and receive a full tuition refund, minus a $39 service charge for each registrant. Cancellations within 48 hours will receive a credit toward another seminar or the self-study package. You may also send another person to take your place
Posted in News| Comments Off on Complying with Fire and Building Codes
Hospital Fire Alarm System Analysis & Design – A Case Study
This case study discusses major design and installation considerations entailed in a complete overhaul of a fire alarm system in a highly critical facility, and it examines life safety features of a fire alarm system in an existing high-rise hospital. Features of the fire alarm system included in the discussion revolve around partial evacuation strategies, private mode signaling, emergency voice and mass notification applications, positive alarm sequencing considerations, distributed antennae for emergency responders retrofitting, and the construction of a fire command center to address the needs of the fire service.
Presenter: Justin Biller, P.E., FSFPEJustin Biller, P.E., FSFPE is the owner and principal engineer for Emerson Graham & Associates, PLC, established in 2015 as a fire protection engineering and code consulting firm with offices in Roanoke, VA and Charlotte, NC. In addition, Justin is an adjunct faculty lecturer for University of North Carolina at Charlotte and Eastern Kentucky University in each of their respective fire protection engineering technology programs. Mr. Biller is also co-founder and technical director of AEGIS, a fire door/barrier management company serving the Mid-Atlantic region. He is a graduate of the master of sciences program in fire protection engineering from Cal Poly and has almost 20 years’ experience in this field.
Posted in News| Comments Off on Hospital Fire Alarm System Analysis & Design – A Case Study
Friday, September 20, 2019 | 8:30 am – 4:30 pm Greensboro-High Point Marriott Airport | Greensboro, NC
At this seminar you will: Enhance your understanding of fire protection and life safety design Explore general requirements and criteria related to occupancy classifications Understand the National Fire Protection Association (NFPA) and North Carolina state codes and standards Learn about exit access, discharge and other components of means of egress Discuss fire protection features and equipment Presented by: Justin Biller, P.E., MCP, CFPS, CLSS-HC, Emerson Graham + Associates, Charlotte, NC
SFPE has recognized 8 of its members as Fellows for 2019. SFPE Fellows represent a distinguished group of members who have achieved a standard of excellence in the profession. Election to Fellow not only recognizes the achievements of fire protection and fire safety engineers as individuals, but also their significant contributions to fire protection engineering and society globally. Out of a total SFPE Membership of over 4,600, there are only 313 fellows. There are 8 members recommended to Fellow by the 2019 Qualifications Subcommittee and approved by the SFPE Board of Directors.
Congratulations Justin Biller, P.E., MSc. FPE, MCP, CFPS, CLSS-HC! Chosen as the new SFPE Fellow, Justin Biller, P.E., is the owner and principal engineer for Emerson Graham & Associates, PLC, established in 2015 as a fire protection engineering and code consulting firm with offices in Roanoke, VA and Charlotte, NC. In addition, Justin is an adjunct faculty lecturer for University of North Carolina-Charlotte and Eastern Kentucky University in each of their respective fire protection engineering technology programs and has taught a host of undergraduate and graduate courses in fire protection systems, building/fire codes, fire dynamics, human behavior in fire and performance-based engineering design. Mr. Biller is also co-founder and technical director of AEGIS, a fire door/barrier management company serving the Mid-Atlantic, and is associated with a forensic consulting firm and volunteer for Roanoke County in work related to post-fire investigations. Justin is a 2014 graduate of the MSc. Fire Protection Engineering program at California Polytechnic State University, and holds registration as a professional fire protection engineer in multiple states on the east coast. He is a Certified Fire Protection Specialist (CFPS) and a Certified Life Safety Specialist for Healthcare Facilities (CLSS- HC) from NFPA. He additionally holds the Master Code Professional (MCP), Certified Building Official (CBO), and Fire Code Specialist (FCS) certifications from ICC. Justin has served on numerous NFPA technical committees including Safety to Life and Alternatives to Life Safety, and likewise on several SFPE committees including the Research, Tools & Methods and Professional Qualifications working on several SFPE guidelines, ABET program evaluation, and the on-going development of the PE exam in fire protection.
Posted in Fire Safety, News| Comments Off on Justin Biller- New SFPE Fellow
See a different side of AEGIS on Instagram. Although we dislike finding doors that are out of compliance, sometimes we just have to shake our heads. Our inspectors find some of the most ingenious examples of how not to repair or modify a fire door. Follow along with us as we share some of our favorite fire door fails. You can follow #FireDoorsSaveLives on Instagram, LinkedIn, Google+ and Twitter to make sure you never miss an update from us.
Directions: Open Instagram & scan the nametag to the left with your smartphone. Then tap FOLLOW. Have fun seeing if you can #SpotTheCodeDeficiency and be the first to offer an approved solution.
Posted in News| Comments Off on Scan to Follow Us on Instagram!
As published in DHI’s Door Security + Safety magazine – December 2018
With obtaining several years of invaluable experience in performing annual NFPA 80 inspections of fire rated doors, our company has identified several key lessons-learned that we thought would be a valuable resource for door and facility professionals to consider.
Fire protection door openings in the occupancies we began performing work in were in much worse condition than initially expected. For example, one facility that our staff surveyed last year assured us ‘we would not find one deficiency in their facility.’ Their best maintenance technician had thoroughly gone through all the doors and signed off that they were 100% compliant. We inspected 98 doors and of that total number 97 failed the NFPA 80 inspection requirements. Was the technician lousy at his job? Not at all – rather he was a fantastic door technician. What was missing was a proper understanding of the applicable code requirements. This high rate of failure has been noted at the majority of facilities following initial annual inspections.
We had the expectation that overall door code-compliance would naturally increase with subsequent annual inspections. While rates did rise, they were not anywhere close to where they were expected to be. Completing repairs to bring the doors into compliance did not guarantee future compliance. Doors are a living part of a building in the sense that every day the components are moving, flexing and being stressed. As hardware reaches the end of its life cycle, inspections accordingly note that things break. Doors, particularly in heavily traveled portions of the building have increased stress due to occupant use, and at times abuse – in healthcare occupancies where many of our inspections occur, carts, beds and equipment take a heavy toll on fire doors and frames. While occupants and user groups in a facility consider it ‘just another door’, as professionals we recognize that the door must be ready to serve as a fire barrier when called upon, and it is imperative to recognize the irreplaceable human lives that are depending on these doors to properly function as required by code.
We have also realized that research into various code application requirements, beyond just NFPA 80 is often necessary. It is thus imperative to seek out competent expertise in building, fire and life safety codes and standards to assist inspectors in applying the appropriate requirements – this may be through a trusted regulatory authority such as a fire or building official or other code consultant.
We would like to highlight some issues we have encountered in the course of annual inspections so as to help highlight some of the complexities of this process:
Does the door have a label? Yes, but did we read it?
What is the barrier rating on the life safety plan? Is it the correct door?
A 20-minute door in a 2-hour barrier wall is incorrect – which is likely obvious. How about a 45-minute door in a 1-hour barrier surrounding a medical gas storage room? A 60-minute door would be required. At times an inspector needs knowledge of codes beyond NFPA 80 to understand the correct application.
What is the required latch throw? (see picture #1)
This label has several qualifications if installed in pairs. Is the correct latch bolt installed?
Where is the door located? (see picture #2)
The label calls for installation in single swing locations only. This label was found on a pair of double egress doors thus voiding the label.
Is a gasket required if there is an ‘S’ on the label? (see picture #3)
It’s not automatic. Only if required by the life safety, fire or building code.
Is the correct hardware installed? (see picture #4)
Sometimes it is noted that cylinder handle-sets are installed on doors labeled for use only with surface mounted hardware. The reverse has also been observed, doors with exit hardware that were not labeled for such.
Is the hardware installed correctly?
What does the manufacturer require? (see picture #5)
Even though the inside of a 90-minute door looks like drywall, plastic anchors are not approved to install exit hardware. Often it is noted that drywall screws or #8 zip screws are holding on hardware where #12 or ¼” through bolts are required.
Why all the empty fastener locations? (see picture #6)
All the required fasteners must be installed. This strike begs a few more questions: The Von Duprin 499F strike is specified when surface vertical rod hardware is installed less bottom rod and necessitates that there is a second part that is installed above the top latch on the door. With it being missing, additional questions are subsequently raised, such as whether there is a fire pin installed, or not? If this is a modification to existing hardware? Does the hardware manufacturer allow the modification? Does the door manufacturer? Have you kept any documentation to show the AHJ that it is an approved modification?
How should it be installed? (see picture #7)
This is an access door in a 2-hour shaft. The four 1-1/4” drywall screws that ‘anchored’ this door were not into any framing! Caulk was literally all that held this door in place. Also notice the huge gap in the drywall around the door frame. This installation failed.
Is this an approved modification?
Can a double acting door be converted? (see picture #8)
Welded steel angle was added to make a stop. In addition, the doors had terrible clearance issues due to the rounded edges of double acting doors. Is this acceptable? The real question is, how was the door and frame tested and can it be proved that the doors will survive for the required fire endurance?
Can we extend a door with a non-compliant bottom clearance? (see picture #9)
A small piece of wood was attached to the bottom of the door. It was hard to spot due to a kick-plate and mop-plate installed on either side of the door covering the extra piece of wood. This is not an approved repair.
Can we field modify a frame for electrified hardware? (see picture #10)
This frame was modified for an electric strike, then had the strike removed. It really shows why field-modification to a frame for this type of hardware is not advisable and will likely not be accepted by the manufacturer. This frame has been severely weakened by the modification.
Can we add parts to make it work? (see pictures 11, 12, 13 and 14)
The adage, ‘necessity is the mother of invention’ certainly holds true in door repair, and nowhere does this seem to be truer than in the installation of magnetic hold-open devices. They are obviously not compliant solutions, but one has to appreciate the ingenuity.
Can we add extra fasteners? (see picture 15)
One can almost hear the installer saying, ‘I’m going to get one of these screws to grab something.’ Again, the question becomes has this hinge been tested this way? Also, has the door been damaged beyond use? Drilling 8 holes in the hinge stile would severely compromise its st
Need a new lock?(see picture 16)
Remove the mortise lock, install an edge guard and new cylinder lock. As one of my instructors at DHI would say, ‘This results in a pile of fire wood.’ This type of modification voids the door label.
Is this an approved application?
Can an edge guard fix a clearance problem? (see picture 17)
We have seen door edge guards installed to solve clearance issues. While not listed to solve clearance issues, it may be a solution for a small clearance issue (ask your AHJ). A couple questions though… Is it rated for use on a fire door? Is it installed per the manufacturer’s instructions? Meaning, we cannot add additional shims behind the edge guard to close a larger clearance issue. The final question has to do with the picture. Does the installation of the edge guard affect how far the latch engages the strike? Clearance issues are not just about how much smoke will get past. It is also about whether or not the latch bolt will stay engaged during a fire. If you have ever seen a video of a fire door test (SDI has one on YouTube) you will realize that the doors pull, bow and twist. If the latch bolt is not long enough, it will allow the door to pop open during a fire.
Its stainless steel, can it be used? (see picture 18)
This is a beautiful frame protector. Is it rated for use on a fire door?
What can I install on my door? (see pic 19 and 20)
We see this often. A mailbox is needed. A coat hook is needed. Some protection for the hardware is needed. We would need to find a product that is rated for use on a fire door.
Creativity at its best. (see picture 21)
This one always makes me smile. Creative, yes. Compliant, no.
Is it damaged beyond use?
How to repair a large hole in the frame? (see picture 22)
We see this often. A magnetic lock is removed leaving behind a large hole in the frame. How would you repair this?
I must hold this door open. (see picture 23)
I sense a battle between the janitors and the maintenance staff. Have the welds broken in the door? Have the clearances been affected? Have the hinge pockets been over stressed and bent or broken?
Looks like a beautiful installation. (see picture 24)
Due to some clearance issues our technician had to remove the hinge. That’s when we found out that the hinge pocket was broken, and the edge guard was all that was ‘holding’ the door together. We have to ensure that any repairs we do will survive a fire and the only way to do that is to test it. We need to know when to say, ‘replace it’.
Can I reuse a door we have in storage? (see picture 25 and 26)
While it is completely acceptable to reuse doors in good condition, we need to make sure all the hardware on the door will match the existing frame conditions. These types of modifications are not permitted.
What to do with a rusted frame? (see picture 27)
Obviously, this frame will need to be replaced due to rust damage. My real question is what are they cleaning the floors with?
The inspectors at our company had a good time putting these examples together. It is a real testament to the creativity of the maintenance staff at these facilities. While some of these repairs would be just fine on a non-rated door, they will cause problems on a fire protection rated door opening. Compliant fire doors are a huge part of our facilities fire protection. If just one door does not perform as specified, many lives could be put at risk, and as such it is critical that we do all we can to make sure our fire doors are ready to do their job.
We can truly see the wisdom in this new code requirement for annual inspections. While in the beginning we may have chafed or balked at the thought of this new requirement, our compliance rates are showing that we needed to do better.
I hope these examples help highlight that an effective inspection really requires three components: 1. Thorough knowledge of the code and how it applies to your facility, 2. Thorough knowledge of proper installation and application of hardware on rated doors and frames, and 3. The ability to effectively communicate what the deficiencies are and what possible solutions there may be. If you find that your facility could use help with inspections, find one of the many DHI trained and certified FDAI’s (Fire & Egress Door Assembly Inspector). Their experience and knowledge will be an invaluable resource for you.
-Mark Waller, FDAI I Managing Director of AEGIS
Posted in Dr. Door| Comments Off on Fire Door Inspections- What are we learning?